This document describes hydraulic performance tests (including cavitation tests) using a small size pump (centrifugal, mixed flow or axial pump, hereinafter referred to as a "model pump").
This document is used for pump acceptance tests with a geometrically similar model pump to guarantee the performance of a large size pump manufactured for practical use (hereinafter, a "prototype pump"). This document, however does not preclude a temporary assembly inspection or other tests on the prototype pump. Moreover, it is preferable to conduct the tests with prototype pumps unless
— the capacity of the pump, namely its flow rate and/or its power input, is beyond the limitations of the test facility, though it is difficult to set a criterion for carrying out a model pump test instead of the prototype pump test in terms of the volume rate of flow or the power input,
— a part of the pump is to be constructed by concrete walls and reproduction of the whole assembly is impractical,
— model tests are specified by the purchaser, or
— it is difficult to carry out the prototype pump test due to any other reasons.
This document applies to performance tests under steady operating conditions corresponding to the prototype pump.
Status: PublishedPublication date: 2019-01
Edition: 1Number of pages: 44
Technical Committee: ISO/TC 115/SC 2 Methods of measurement and testing
- ICS :
- 23.080 Pumps
Buy this standard
|std 1 166|
|std 2 166||Paper|
ISO/TR 19688:2019Stage: 60.60
Got a question?
Check out our FAQs
Monday to Friday - 09:00-12:00, 14:00-17:00 (UTC+1)
Keep up to date with ISO
Sign up to our newsletter for the latest news, views and product information.